Originally Posted by 8 Builder
Don't suppose the contractor cares which way the electricity flows through it. It just closes a starter meter circuit, right? Has anyone else seen this? Sorry. TinyPic would not upload the picture.
Electrically it doesn't matter for the start
relay (for the master relay it does), but the orientation is specific to avoid the possibility of high G's causing the plunger to move and energize the starter motor.
I am not familiar with an interference problem if mounted per plans.